Enterprise Plus LCD 750VA 600Watts
750 VA Line Interactive Rack/Wall/Tower UPS with 8 Outlets 750VA/600W 120 VAC line interactive, rack/wall/tower UPS designed for critical, power-sensitive electronic encironments Does not feature a connection for external battery packs 0.8 Power factor increases the capacity of the unit without migrating to larger models Load shedding extends time of critical applications by removing power to non-essential devices Independent battery bypass allows UPS to provide voltage regulation with surge and spike protection on AC power even when batteries are weak or dead Floor-standing tower and 19-inch rack mount hardware included Optional installation kits for 23-inch racks/cabinets and wall mount are available Small form factor with 2U size Simultaneous DB9, USB, and SNMP communications (SNMP card sold separately) SentryHD UPS monitoring and control software included Easy to read LCD display Dedicated remote Emergency Power Off (EPO) port RoHS2 compliant Connected equipment covered with Minuteman $100,000 protection plan Applications: workstation, network/server, phone and security systems Voltage Range(VAC): 80-164 Frequency: 50/60Hz +/- 6Hz autosensing Phase: Single Waveform: true sine waveInput Plug Type: 5-15P Capacity (VA/W): 750/600 Transient Response (ms): +/- 10% at 100% load change in 30ms Runtime (minutes): 8 full load, 17 half load Fully Protected Outlets: 8 5-15R RJ11 Protection: Yes RJ45 Protection: Yes Serial DB9 Ports: 1 Dry Contact Ports: 1 USB Ports: 1 Surge Energy Rating (Joules): 1000 Number of Internal Batteries: 1 Battery Part: BM0029 LCD Display Indicators: input/output voltage and frequency, UPS and battery mode/status, load capacity, estimated runtime Operating Temperature: 0-40 degrees Celsius
Featured:Line interactive rack/wall/tower ups with 8 outlets|Simultaneous db-9, Usb and snap (snap card sold separately)|Ups monitoring and control software
|Brand Name||MINUTEMAN UPS|
Write a reviewYour Name:
Note: HTML is not translated!
Rating: Bad Good
Enter the code in the box below: